Does Von Duprin's factory refurbish exit devices?
Von Duprin does not offer a service to refurbish exit devices at the factory.Replaceable service items for some exit device parts are available for sale.Please contact technical product support a...
Exit Devices | Exit Devices » Cross Bar | Exit Devices » Mechanical Accessories
Can I cut a Von Duprin mullion from the bottom rather than the top?
It is not recommended to cut a mullion from the bottom as this will lower any strike templating on the mullion body cause the strike and exit device to be misaligned....
Exit Devices » Mechanical Accessories » Mullion | Exit Devices » Mechanical Accessories » Mullion » Von Duprin
What mullions should be used with XP devices?
The Von Duprin XP98/99 device uses a different strike than standard 98/99 device.
The 909 strike is for non fire rated XP devices and the 954 strike is for the fire rated XP device.
Exit Devices » Mechanical Accessories » Mullion » Von Duprin | Exit Devices » Touch Bar » 98/99 Series » Von Duprin
What electric strikes can be used with the Von Duprin aluminum mullions?
Aluminum mullions 5654 or 5754 are not designed to accept any electric strike including 6300 surface mounted electric strike....
Exit Devices » Mechanical Accessories » Mullion » Von Duprin | System Components » Electric Strikes » 6000 Series » Von Duprin | System Components » Electric Strikes » 6300 Series » Von Duprin